for Seneca, SC
Our Reviews by City
Jan - Seneca, SC 29672
Great experience of installing hvac
Kevin - Seneca, SC 29678
Chris was excellent- he listened to what I wanted and showed me what was necessary and what alternatives there were. I could not be more pleased with his professional manner and attention to detail in the quote he provided
Larry - Seneca, SC 29672
Steve - Seneca, SC 29672
We have a complicated system and Andrew sticks with it until the problem is solved!
Did an excellent job of my fall service on my two new units
Joe M of Seneca, SC - Seneca, SC 29672
Robert did an excellent job servicing my two new units. He was very pleasant and knowledgeable about my two York high tech units.
Removed old HVAC system and installed a new two stage inverter compressor heat pump unit with York electric furnace in attic. Installed two MERV13 pleated air filter cabinets, new supply and return air plenums insulated, auxiliary drain pan with two water safety devices, linehide up outdoor wall to camouflage new 1-1/8”x3/8” copper refrigerant lineset, new breakers, outdoor unit pad, topped off with a color touch screen WiFi thermostat connected to the homeowner’s phone for convenient operation
Changed out bad thermostat
Quote for rewire of a circuit
Completed diagnostic on goodman unit
Completed drain repairs
Lennox Heat Pump system not coming on at all. System controlled by Arzel zoning airboss control system with three thermostats. Correct control system faults and ice control sensor fault for proper heat pump defrost controls. Now functioning normally after significant repairs. Verify York heat pump operating normal and efficiently.
Repaired no heat pump operation on a York/Lennox dual fuel system. Rodent damaged temperature sensor causing issue. Found leaking coil on Lennox heat pump and recharged adding internal sealers. Completed semi annual maintenance on both systems.
Failed blower system on Goodman R22 heat pump. Air not circulating. Repaired with new specified components for warm air from air handler.
Complete fall maintenance on york heat pump system, finding that exhaust removal system on outdoor unit had failed. Renovated exhaust system and performance tested system.
Fall maintenance on two York split heat pump systems.